View and Download Dixell XR20C installing and operating instructions online. Digital controller with off cycle defrost. XR20C Controller pdf manual download. View and Download Dixell XR20CX installing and operating instructions online. Digital controller with off cycle defrost. XR20CX Thermostat pdf manual. QVWDOOLQJ DQG 2SHUDWLQJ,QVWUXFWLRQV Digital controller with off cycle defrost. SET: To display target set point; in programming mode it selects a.
|Published (Last):||2 October 2012|
|PDF File Size:||15.27 Mb|
|ePub File Size:||17.54 Mb|
|Price:||Free* [*Free Regsitration Required]|
CCS Set point for continuous cycle: Instrument XR20CX shall be mounted on vertical panel, in a 29×71 mm hole, and fixed using the special bracket supplied. XR20CX panel mounting in a 71x29mm panel cut-out Protection: Ptb Map code Dixell S. Page of 4 Go. Installing and Operating Instructions. This manual is part of the product and should be kept near zr20c instrument for easy and. The instrument shall not be used for purposes different from those described hereunder.
Check the supply voltage is correct before connecting the instrument. Do not expose to water or moisture: Fit the probe where it is not accessible by the End User.
The instrument must not be. In case of failure or faulty operation send the instrument back to the distributor or to. Consider the maximum current which can be applied to each relay see Technical Data. Ensure that the wires for probes, loads and the power supply are separated and far. In case of applications in industrial environments, the use of mains filters our mod. Model XR20C, format 32 x 74 mm, is a digital thermostat with off cycle defrost designed for.
It provides a relay output to drive the. The digital input can operate as. The instrument is fully configurable through special parameters that can be easily.
electronic controller DIXELL XR20C-5N1C1 378018
In case of fault in the thermostat probe the start and stop of the compressor are timed through. Defrost is performed through a simple stop of the compressor. Parameter “IdF” controls the. To display target set point; in programming mode it selects a parameter or confirm. To see the max. DOWN To see the min stored temperature; in programming mode it browses the. Each LED function is described in the following table. The “Lo” message will be displayed followed by the minimum temperature recorded.
By pressing the 8 key again or by waiting 5s the normal display will be restored. The “Hi” message will be displayed followed by the maximum temperature recorded. By pressing the 9 key again or by waiting 5s the normal display will be restored. Hold press the SET key for more dxell 3s, while the max.
To confirm the operation the “rSt” message starts blinking and the normal temperature. Push and immediately release the SET key: Push and immediately release the SET key or wait for 5 seconds to. Push the SET key for more than 2 seconds to change the Set point value.
To change the Set value push the 9 or 8 arrows within 10s. To memorise the new set point value push the SET key again or wait 10s.
DIXELL XR20CX INSTALLING AND OPERATING INSTRUCTIONS Pdf Download.
Push the DEF key for more than 2 seconds and a manual defrost will. Add to my manuals Add.
Page 2 Energy Saving cycle. Page 4 Ptb Map code Dixell S. Comments to this Manuals Your Name. Enter text from picture: By pressing ‘print’ button you will print only current page. To print the manual completely, please, download it.
Don’t show me this message again.
Got it, continue to print. Don’t have an account?